What is a reasonable device number on a BACnet MSTP chain?
A site reported 50 MSTP devices attached to a BACnet/IP to MSTP router (like our Cimetrics B6000). Device chain response was slow…taking as much as three or four minutes to get under ten points from each device.
MSTP and many RS485 communications networks allow 250 addresses with data rates up into the 100 kBaud range and line lengths to a maximum of 1200 m. But having all of these maximums at once is almost never practical.
BACnet MSTP itself only allows 127 master devices in its address space. But even approaching that number would generally be problematic for the protocol and the underlying RS485 data-link.
The RS485 data-link as a bus topology needs proper wire type and proper biasing and termination to perform properly. RS485 transceivers have a loading factor which limits how many can be connected to the bus. For full-load transceivers more than about 16 are not a good idea, and even with modern quarter or sixteenth load transceivers, there can be problems. Reliable operation of nodes is often specified at moderate data rates around 10 kBaud and moderate line length of around 100m. These and other factors make it reasonable to stay within a 32 device limit. One can see such device number limits due to underlying RS485 issues with networks like JCI N2 and Siemens P1 as well.
Even when one has good RS485 wiring at reasonable speeds and distances and one has a reasonable number of nodes (say around 16), one can still get sluggish performance with MSTP with poorly tuned time-outs and MAX_MASTER.
Staying away from address 0 and 1 is nowhere a part of any standard, but it helps avoid defaults configuration and other implementation issues. If one has sixteen devices then put any router at 2 (or MAX) and number the devices 3,4,5…through MAX-1) and THEN set MAX_MASTER at MAX+3 for a little (bit not too much) headroom.
For an MSTP segment with 50 devices subdivide into at least two MTSP RS485 segments by adding routers like the Cimetrics B6000s. And for that matter for Modbus chains like connected with a Cimetrics B6030. Staying below 16 nodes per segment is safest. Check your RS485 wiring for good characteristics and keep your speeds and lengths moderate. Understand timing and MAX_MASTER issues.
And when you think that you are experiencing MS/TP performance problems, a network protocol analyzer such as the Cimetrics BAS-o-matic can help you to diagnose the problems.
Comments will be approved before showing up.
cimetrics.com Legal Terms and Conditions
June 29, 2016
cimetrics.com (the "Site") is owned by Cimetrics Inc. ("Cimetrics").
PLEASE READ THESE TERMS AND CONDITIONS CAREFULLY BEFORE USING THIS SITE. YOU MAY NOT USE THIS SITE IF YOU DO NOT ACCEPT THE TERMS AND CONDITIONS.
The information herein provided is for general informative purposes only, and no warranties or representations are made with respect thereto. The information may contain inaccuracies or typographical errors. The information provided is subject to change at any time, and without notice. Changed information may include, but is not limited to, technical specifications and pricing. Binding declarations are only given after detailed enquiries.
BECAUSE THE INFORMATION IS NOT WARRANTED, ALL LIABILITY FOR THE ACCURACY OF THE INFORMATION IS EXPRESSLY EXCLUDED.
If you have been given a Password in order to gain access to certain information on this Site, or any other affiliates’ website, then you agree, as a condition of receiving said Password, that you shall keep the Password confidential. You shall only disclose the Password to your employees or agents who have a need to know. You are solely responsible for all activities that occur using your Password.
If you become aware of any unauthorized use of your Password, you agree to notify Cimetrics immediately. Cimetrics reserves the right to revoke your Password access at any time for any reason whatsoever.
Copyrights and Trademarks
All information provided on the web pages of Cimetrics.com is protected by copyright. It is prohibited to copy, process, modify or commercially distribute this information without the express written permission of Cimetrics.
Analytika, Infometrics, Metermetrics, BACstac, BACstac/DN, and BAS-o-matic are trademarks or registered trademarks of Cimetrics. The Analytika, Cimetrics, Infometrics and Metermetrics logos are trademarks or registered trademarks of Cimetrics. All other trademarks are owned by their respective companies.
Links to Other Websites