Do you know which devices have duplicate addresses on a network? Do you know where to look if there is no activity on the BACnet MS/TP network?
To answer these and other similar questions, you need to have the appropriate tools: One to discover all the devices on a network (e.g. BACnet Explorer) and one (e.g. BAS-o-matic or Wireshark) to actually capture the packets.
But first, what is BACnet MS/TP? BACnet defines the MS/TP (master-slave/token-passing) as a network designed to run at speeds of 115,200 bits per second or less over twisted pair wiring. MS/TP is widespread, easy to set up, and doesn't require expensive infrastructure. As with any other network, problems may arise. In the article "Troubleshoot MS/TP Network" we outline six reasons for troubled communication on a BACnet MS/TP network. If you work with this network, you need to monitor its health and troubleshoot if there are any problems.
We have a special device for this task called U+4 USB to BACnet MS/TP Interface. The U+4 device helps connect a computer or laptop to a BACnet/MSTP network. The USB port on the U+4 connects to the PC, and the screw terminals help connect the BACnet/MSTP network to the U+4 hardware. This allows applications like BACnet clients (e.g., Cimetrics BACnet Explorer) and diagnostic programs (e.g., Cimetrics BAS-o-Matic or Wireshark) access to the BACnet/MSTP network.
Using a simple adapter may seem like an obvious choice to access the network, but we have identified several problems that may arise when using such devices. First, simple adapters convey a stream of bytes from the wire to the Windows Operating System and even transmit it reliably. But, inevitably, they cannot keep track of the timing of the bytes which may lead to incorrect packet assembly or even phantom packets. This can occur more frequently if the network is noisy and bytes get distorted during transmission. Lastly, although you can monitor data through a simple adapter you cannot transmit the data.
There are also solutions that use USB to UART converters with the MS/TP implementation running inside of a PC. Because Windows is not a real-time system, such implementations cannot work reliably and may create havoc on the MS/TP network when they respond outside of the real-time requirements. The U+4 has a microprocessor that handles the time-critical functionality on the MSTP network.
Once installed, the U+4 mimics an Ethernet card. The user can choose this newly installed “Ethernet” card for communications with a BACnet MS/TP network.
Comments will be approved before showing up.
cimetrics.com Legal Terms and Conditions
June 29, 2016
cimetrics.com (the "Site") is owned by Cimetrics Inc. ("Cimetrics").
PLEASE READ THESE TERMS AND CONDITIONS CAREFULLY BEFORE USING THIS SITE. YOU MAY NOT USE THIS SITE IF YOU DO NOT ACCEPT THE TERMS AND CONDITIONS.
The information herein provided is for general informative purposes only, and no warranties or representations are made with respect thereto. The information may contain inaccuracies or typographical errors. The information provided is subject to change at any time, and without notice. Changed information may include, but is not limited to, technical specifications and pricing. Binding declarations are only given after detailed enquiries.
BECAUSE THE INFORMATION IS NOT WARRANTED, ALL LIABILITY FOR THE ACCURACY OF THE INFORMATION IS EXPRESSLY EXCLUDED.
If you have been given a Password in order to gain access to certain information on this Site, or any other affiliates’ website, then you agree, as a condition of receiving said Password, that you shall keep the Password confidential. You shall only disclose the Password to your employees or agents who have a need to know. You are solely responsible for all activities that occur using your Password.
If you become aware of any unauthorized use of your Password, you agree to notify Cimetrics immediately. Cimetrics reserves the right to revoke your Password access at any time for any reason whatsoever.
Copyrights and Trademarks
All information provided on the web pages of Cimetrics.com is protected by copyright. It is prohibited to copy, process, modify or commercially distribute this information without the express written permission of Cimetrics.
Analytika, Infometrics, Metermetrics, BACstac, BACstac/DN, Secured by Cimetrics™ and BAS-o-matic are trademarks or registered trademarks of Cimetrics. The Analytika, Cimetrics, Infometrics and Metermetrics logos are trademarks or registered trademarks of Cimetrics. All other trademarks are owned by their respective companies.
Links to Other Websites