Multiply the number of devices*, by the length of the line in km, by the speed of operation in kBaud, by a “problem factor”, and keep the number below thirty.
The star (*) above on number of devices is to warn that one generally deals in quarter load or better devices. If you are using older full-load RS485 devices then consider each device as four devices.
The problem factor is a number which is usually unity (1) when all the line characteristics are well conditioned. Double it if there is poor biasing. Double it for poor termination. Double it again if cable runs are close to motors or transformers. Double it for improper capacitance. Double it for poor twisting of the cable. Double it for potential ground faults like poor/weak or multiple grounding.
BACnet MS/TP and many RS485 communications networks allow 250 addresses with data rates up into the 100 kBaud range and line lengths to a maximum of 1200m. But having all of these maximums at once is not practical.
The rule of thumb is key when connecting chains of Modbus RTU meters to Cimetrics B6030 EasyMap to BACnet or Cimetrics B2000 router to ModbusTCP; or when connecting chains of BACnet MS/TP devices for use with a Cimetrics B6000 BACnet/IP to MS/TP router.
Comments will be approved before showing up.
cimetrics.com Legal Terms and Conditions
June 29, 2016
cimetrics.com (the "Site") is owned by Cimetrics Inc. ("Cimetrics").
PLEASE READ THESE TERMS AND CONDITIONS CAREFULLY BEFORE USING THIS SITE. YOU MAY NOT USE THIS SITE IF YOU DO NOT ACCEPT THE TERMS AND CONDITIONS.
The information herein provided is for general informative purposes only, and no warranties or representations are made with respect thereto. The information may contain inaccuracies or typographical errors. The information provided is subject to change at any time, and without notice. Changed information may include, but is not limited to, technical specifications and pricing. Binding declarations are only given after detailed enquiries.
BECAUSE THE INFORMATION IS NOT WARRANTED, ALL LIABILITY FOR THE ACCURACY OF THE INFORMATION IS EXPRESSLY EXCLUDED.
If you have been given a Password in order to gain access to certain information on this Site, or any other affiliates’ website, then you agree, as a condition of receiving said Password, that you shall keep the Password confidential. You shall only disclose the Password to your employees or agents who have a need to know. You are solely responsible for all activities that occur using your Password.
If you become aware of any unauthorized use of your Password, you agree to notify Cimetrics immediately. Cimetrics reserves the right to revoke your Password access at any time for any reason whatsoever.
Copyrights and Trademarks
All information provided on the web pages of Cimetrics.com is protected by copyright. It is prohibited to copy, process, modify or commercially distribute this information without the express written permission of Cimetrics.
Analytika, Infometrics, Metermetrics, BACstac, BACstac/DN, and BAS-o-matic are trademarks or registered trademarks of Cimetrics. The Analytika, Cimetrics, Infometrics and Metermetrics logos are trademarks or registered trademarks of Cimetrics. All other trademarks are owned by their respective companies.
Links to Other Websites