A problem often experienced by our product users, analytics or consultative clients is broken BACnet network. It happens more times than you think— it is usually about customers trying to get from TCPIP subnet to subnet without (the usually banned) global broadcasts between subnets.
Often there is a BBMD or FD involved and often it is broken.
“Broken” can mean some or all devices involved:
A – Support only a “local” mode. While they can do global broadcasts, they themselves do not support directing those broadcasts. They need external BBMD support.
B – Have FD or BBMD support - but status and administrative access do not allow one to see or configure said FD or BBMD.
C - Claim to be a BBMD or FD but it does not actually function as such. Sometimes because of a complex configuration process – or simply the type of broadcast transport is broken.
D – function fine as a BBMD or FD but have obscure or complex UI, or deliver no status information in real-time.
E – Are mixed in capabilities A-D in a complex array of different devices. Though some or all might work, they are very complex to manage – due to different function, interfaces and nomenclature.
Note that software BACnet network devices can add another layer of complexity where execution privileges, network access and OS firewall issues can cause difficulties. The solution to this problem will be a standalone BBMD – e.g. Cimetrics B3060 - running on embedded hardware platform with a network OS. Just turn off or remove all your problem BBMDs, and place the standalone BBMD in each and every isolated subnet. B3060 Configuration steps involved:
- Open up FD on each form allowed remote access (allow FD and get status via FDT).
- Point each unit at all other units with which you wish to share broadcasts. (Fill the BDT with a mesh of your design in your control).
- No “extra” interfaces or networks to complicate setup.
- Operate seamlessly. Enjoy.
Comments will be approved before showing up.
cimetrics.com Legal Terms and Conditions
June 29, 2016
cimetrics.com (the "Site") is owned by Cimetrics Inc. ("Cimetrics").
PLEASE READ THESE TERMS AND CONDITIONS CAREFULLY BEFORE USING THIS SITE. YOU MAY NOT USE THIS SITE IF YOU DO NOT ACCEPT THE TERMS AND CONDITIONS.
The information herein provided is for general informative purposes only, and no warranties or representations are made with respect thereto. The information may contain inaccuracies or typographical errors. The information provided is subject to change at any time, and without notice. Changed information may include, but is not limited to, technical specifications and pricing. Binding declarations are only given after detailed enquiries.
BECAUSE THE INFORMATION IS NOT WARRANTED, ALL LIABILITY FOR THE ACCURACY OF THE INFORMATION IS EXPRESSLY EXCLUDED.
If you have been given a Password in order to gain access to certain information on this Site, or any other affiliates’ website, then you agree, as a condition of receiving said Password, that you shall keep the Password confidential. You shall only disclose the Password to your employees or agents who have a need to know. You are solely responsible for all activities that occur using your Password.
If you become aware of any unauthorized use of your Password, you agree to notify Cimetrics immediately. Cimetrics reserves the right to revoke your Password access at any time for any reason whatsoever.
Copyrights and Trademarks
All information provided on the web pages of Cimetrics.com is protected by copyright. It is prohibited to copy, process, modify or commercially distribute this information without the express written permission of Cimetrics.
Analytika, Infometrics, Metermetrics, BACstac, BACstac/DN, and BAS-o-matic are trademarks or registered trademarks of Cimetrics. The Analytika, Cimetrics, Infometrics and Metermetrics logos are trademarks or registered trademarks of Cimetrics. All other trademarks are owned by their respective companies.
Links to Other Websites