The BR2-A - BACnet router provides routing between BACnet/IP, and BACnet ARCNETnetworks. This allows integrators to mix and match these two BACnet network datalink technologies within a single BACnet Internetwork.
The BR2 Router is enclosed in a metal case that can be mounted standalone or in a 1U rack space. The unit has one ARCNET connector and one Ethernet 10/100 RJ45 connector.
The ARCNET connector is an industry standard BNC connectore for 93 Ohm (RG62) cable. It operates at the standard 2.5 Mbps and by default uses normal timeouts though it can be set for one of the three available ARCNET extended timeouts settings used in long cable run segments. Logically and physically 254 devices can be addressed. The ARCNET is not terminated internally to give the user flexibility in connections and topologies used.
The Ethernet port uses a standard shielded RJ45 connector with integral LEDs. Connection status can quickly be ascertained from the Link and Activity LEDs on each interface.
An embedded web server allows for commissioning and configuration and troubleshooting via a standard web browser. A power LED is present along with the LEDs for interface status on each interface.
Flexible routing between:
IP network support:
Regulatory Compliance: FCC and CE marked
BACnet has the same protocol for the monitoring, automation and field levels. It is unified top to bottom. BACnet field controllers with direct I/O and application specific features (B-ASC) can communicate all the way up to BACnet/IP Operator Workstations (B-OWS) and BACnet Building Controllers (B-BC).
In order to interconnect such levels, a BACnet Router is needed. The Cimetrics BR2-A is such a BACnet Router. For BACnet/IP the interface is 10/100 Half/Full Duplex RJ45 standard Ethernet station-side. The ARCNET side is 2.5 Mbps using standard 93 Ohm RG62U coaxial cable.
The BACnet/IP port on the BR2-A connects to the network Ethernet/TCPIP port using a standard CAT5 cable. The ARCNET port connects to the target BACnet ARCNET LAN (93 Ohm RG62U Coaxial cable . The BR2-A can be powered from any 120VAC source. The BR2-A is setup using its embedded webpages.
The ARCNET LAN must have a BACnet Network Number unique from the BACnet Network Number assigned to the BACnet/IP network connection. Nothing precludes the use of multiple BR2-A routers in the same ARCNET network as long as unique BACnet network (and ARCNET LAN MAC) assignments are made for each created BACnet/IP configuration access network.
Multiple BACnet Routers can reside within the same BACnet internetwork. A group of ARCNET devices located along an ARCNET LAN, spread in any fashion which adheres to the ARCNET cabling rules, can be bridged to a BACnet/IP network with a BACnet Router. So too can any others like ARCNET, MSTP (or any supported BACnet datalink) be attached using another BACnet Router.
This means of extension is often better than extending existing ARCNET (or MSTP) networks using repeaters. It can also help alleviate LAN loading problems with token collisions, node numbers and cable lengths.
The BACnet/IP port on the BR2-A connects to the main network Ethernet/TCPIP port using a standard CAT5 cable. The ARCNET port connects to the target BACnet ARCNET LAN (93 Ohm RG62 Coaxial cable). The BR2-A can be powered from any 120VAC source. The BR2-A is setup using its embedded webpages.
The ARCNET LAN must have a BACnet Network Number unique from the BACnet Network Number assigned to the BACnet/IP network connection. Nothing precludes the use of multiple BR2-A routers ion the same ARCNET network as long as unique BACnet network (and ARCNET LAN MAC) assignments are made for each created BACnet/IP configuration access network.
To commission BACnet ARCNET devices one has generally been forced to use a special PC hardware ARCNET interface to communicate with the ARCNET RS485 or Coaxial LAN. The secret is that most BACnet ARCNET software can be run against BACnet/IP and communicate via BACnet Routing to BACnet ARCNET to achieve this configuration/setup connectivity. The Cimetrics BR2-A can accomplish this connectivity. The BACnet/IP port on the BR2-A connects to the PC’s Ethernet/TCPIP port using a standard CAT5 cable. The ARCNET port connects to the target BACnet ARCNET LAN (93 Ohm RG62 Coaxial cable). The BR-A can be powered from any 120VAC source.
The BR2-A is setup using its embedded webpages. The baud rate of the BACnet ARCNET port is setup to match the baud rate and network number of the existing ARCNET LAN.
The ARCNET LAN must have a BACnet Network Number unique from the BACnet Network Number assigned to the BACnet/IP network connection created by the PC connection. Nothing precludes the use of multiple BR2-A routers ion the same ARCNET network as long as unique BACnet network (and ARCNET LAN MAC) assignments are made for each created BACnet/IP configuration access network.
cimetrics.com Legal Terms and Conditions
June 29, 2016
cimetrics.com (the "Site") is owned by Cimetrics Inc. ("Cimetrics").
PLEASE READ THESE TERMS AND CONDITIONS CAREFULLY BEFORE USING THIS SITE. YOU MAY NOT USE THIS SITE IF YOU DO NOT ACCEPT THE TERMS AND CONDITIONS.
The information herein provided is for general informative purposes only, and no warranties or representations are made with respect thereto. The information may contain inaccuracies or typographical errors. The information provided is subject to change at any time, and without notice. Changed information may include, but is not limited to, technical specifications and pricing. Binding declarations are only given after detailed enquiries.
BECAUSE THE INFORMATION IS NOT WARRANTED, ALL LIABILITY FOR THE ACCURACY OF THE INFORMATION IS EXPRESSLY EXCLUDED.
If you have been given a Password in order to gain access to certain information on this Site, or any other affiliates’ website, then you agree, as a condition of receiving said Password, that you shall keep the Password confidential. You shall only disclose the Password to your employees or agents who have a need to know. You are solely responsible for all activities that occur using your Password.
If you become aware of any unauthorized use of your Password, you agree to notify Cimetrics immediately. Cimetrics reserves the right to revoke your Password access at any time for any reason whatsoever.
Copyrights and Trademarks
All information provided on the web pages of Cimetrics.com is protected by copyright. It is prohibited to copy, process, modify or commercially distribute this information without the express written permission of Cimetrics.
Analytika, Infometrics, Metermetrics, BACstac, BACstac/DN, and BAS-o-matic are trademarks or registered trademarks of Cimetrics. The Analytika, Cimetrics, Infometrics and Metermetrics logos are trademarks or registered trademarks of Cimetrics. All other trademarks are owned by their respective companies.
Links to Other Websites